Generac 17kw stator and rotor repair Woodinville Samammish, WA. Look closely and you can see the damaged stator in the picture on the right. This type of repair isn’t inexpensive but in this case proved to be a better value that a new generator. After about 3 years the generator just stopped producing power
Although it looks small in the picture this brand new rotor is very heavy.
The customer was disappointed this repair wasnt covered under warranty. During the repair we were suprised to find what caused the generator failure in the first place. Pictured above is a set of keys that fell inside the case of the generator and eventually was sucked inside the stator and rotor. It bent the set of keys and damaged the internal stator and rotor to the point of failure.